Gasoline & diesel generator auto start
Using the Be1 generator auto start module you can make a cost-effective generator control panel. It is suitable for gas and gasoline engines up to 15kVA. It directly interfaces with flywheel generator or standard belt driven charger alternator as well. You can connect any kind of analog sensor to get Oil Pressure, Engine Temperature and Fuel Level measurements. You can connect a magnetic pickup if necessary. I WANT TO CONNECT THE GENERATOR TO MY HOUSE
PURCHASE BE1 FREE SHIPPING 128€
Use the Be1 auto start kit. You have only to add two automotive relays, some wires & terminal block. By using the configurable IN/OUTS lines, you can arrange the controller for any automatic configuration. It has a small size IP65, 96x96mm and operates in between -30°C and +70°C.
BE1 GSM KIT FEATURES
GET NOTIFICATIONS ABOUT ALARMS AND STATUS
GET NOTIFICATIONS ABOUT FUEL CONSUMPTION
START & STOP THE GENERATOR USING MOBILE
READ ENGINE & GENERATOR INSTRUMENTS
CHANGE MODE OF OPERATION FROM MOBILE
SIMPLE PLUG AND PLAY READY FOR USE
Be1 front panel description
The front panel of this generator auto start is extremely intuitive. Thanks to the double set of start-stop buttons, we guarantee the Be1 for at least 2 millions of start stop operations OPEN THE DESCRIPTION PAGE
The Be1 auto start is suitable for gasoline engine
The Be1 Auto Start Module is suitable for gasoline engines. It directly interfaces with the flywheel generator and provides an output specially designed to stop a gasoline engine. Open the AUTO START GENERATOR CIRCUIT page.
Be1 auto start module specifications
Battery supply voltage: 5.5Vdc to 36Vdc. Supply current: 10 mA to 80mA. Inputs: digital (switch) or analog (0-1000 OHM).
Dimensions: 96X96X 47(mm). Panel Cut-out: 91mm X 91mm. Ingress protection: IP65. Outputs: 300mA, NPN short circuit proof.
Operating temperature range: -30 deg C up to +70 deg C. Humidity range: 5% up to 95% non-condensing.
Weight: 350 gr., Vibration: 40mm/sec. Pick-up Input: Voltage input: 2 - 60Vac; 0-10KHz
Generator Monitoring: Operating up to 600Vac. Accuracy: +/- 1,5%. Frequency: 20-70Hz
Manual mode of operation
A) - Push one of the [ I ] push buttons until the display indicates the message [MAn] and all LEDs illuminate; release the button.
B) - Push one of the [ I ] push buttons until engine starts . When the engine is running, the green LED 'START-ON' will illuminate.
C) - To stop the engine, push the [ O ] push button until the [StOP] message appears on the display.
If the engine has already stopped, it is possible to cancel the STOP sequence by pressing the [ O ] push button. Push [ O ] when the engine is not running if you want to shutdown the panel.
Auto mode of operation
Push the [AUTO] push button until the yellow LED 'AUTO' on the button will illuminate (*). The engine starts when you activate the input configured as 'Remote Start Input'. In the same way, the engine stops when you deactivate the 'Remote Start input'. In AUTO mode of operation, the Be-1 will periodically test the engine if you properly programmed the scheduler or the so called 'Periodic Auto Start'. During this test, the yellow LED AUTO will continue to blink.
Please note that Be1 stores, in a 'NON VOLATILE MEMORY', the AUTO mode of operation status. This means that in case you remove and re-apply the DC supply, the Be1 will automatically enter the AUTO mode of operation.
To exit the AUTO mode of operation, you can push the [AUTO] push button for a short time; the Be1 will enter the MANUAL mode of operation. You can directly push one of the  push buttons. In this case the Be1 will directly enter the OFF mode of operation.
Note(*): if the display blinks indicating the message [ALAr.], consult section 8.0 of the user manual. You are required to cancel the alarm in the first place before using the AUTO mode of operation.
The Be1 generator auto start kit features Shutdowns (the engine stops) and Warnings (the engine will continue to run). It informs you about an alarm via:
A) - a general indication of alarm by means of the message [ALAr.] on the display
B) - 4 configurable outputs with several options for each
C) - 4 LEDs indicating Oil pressure, Temperature, Fail to start and Over speed shutdown.
D) - coded display messages about warnings and shutdowns
E) - an [ACK] push button to silence the Horn
To browse the alarm memory push the [→] pushbutton. In order to display the details of the alarm, push the [ ? ] push button. To clear the alarm from the panel, remove the cause of the alarm and then press the [ O ] push button.
ALL ABOUT BELT ALTERNATOR MONITORING
The Be1 automatically terminates the crank when the engine starts running. The Be1 provides an excitement current for the charger alternator. When the engine is not running, the voltage of the terminal D+/WL is 0V (in your car, before starting the engine, the red 'DYMANO LAMP' turns on). As soon as the Be1 starts the engine, a voltage appears in the D+/WL terminal and when the engine runs normally, the voltage of the D+/WL terminal increases by up to 13-14 V (in your car, having one side of the lamp connected to the battery plus, the red 'DYNAMO LAMP' in the dashboard turns off ). The safest point to terminate the crank is in between 6V to 10V. In case of a gasoline engine the belt alternator is not normally available. In this case you are required to connect the engine running detect circuit in a 'floating mode' as indicated in this wiring diagram.
Remote Control Monitoring
In order to remotely control the generator, we recommend that you use our MODBUS-USB converter. You can connect a computer up to 1000 m far away via a shielded twisted pair cable. You can monitor and control your generator by running our free of charge software for Remote Control Monitoring BE1 V1.6. Contact us to get a free of charge copy of the software.
Reading the Event-History Log
The Be1 features an Event History register able to records the last 100 shut-downs. To read the contents of the Event History, follow the instructions:
A) – Remove the DC power supply (battery voltage)
B) – Push and hold the [?] pushbutton
C) – Apply the power supply (holding the [?] pushbutton)
D) – Release the [?] pushbutton when the display turns on
E) – The display will indicate the the last event via the message [E 01]. Push the the [?] push button to display the name of the Event (see table 4.10 in the installation manual)
F) – You can select [E 01] (the last event) up to [E100] (the oldest event) using the [←] and [→] push buttons.
G) – To display the code of the Event, push the [?] pushbutton (see table 4.10 in the installation manual).
It is not possible to cancel the Event History. You are required to cancel the all memory (see instructions on the installation manual)
HOW ARE YOU TODAY?
You are fine! We create our own environment. My first attitude is to design electronic controllers. I am doing this since 1980. This is my mission! What is your mission? My second passion is about QUANTUM PHYSICS and QUANTUM MECHANICS. My third passion is about the mechanics of personal development. You can grow day by day by following recommendations released from healty people. They share their experiences in life. Hope you enjoy my video collection.